Diagnosis of insulation conditions : Interpretation of partial discharges from φ-q-n pattern, pulse-sequence and pulse waveform
Sch. of Electr. Eng. & Inf., Inst. Teknol. Bandung, BandungDOI: 10.1109/CMD.2008.4580230 Conference: Condition Monitoring and Diagnosis, 2008. CMD 2008. International Conference on
Source: IEEE Xplore
Appearance of electrical discharges in high voltage apparatuses with reasonable magnitude and frequency can be interpreted as abnormal condition. The discharge may take place in several types. Firstly, corona discharges which represents abnormal electric stress on a conductor. Secondly, void discharge which represents discharge take place in a gas filled void in solid or liquid insulation. Thirdly, treeing discharge which takes place in tree channels inside a solid insulation. This paper reports experimental results on the three kinds of discharges. The analysis was focused on the phi-q-n pattern, the time sequence between consecutive pulses and the waveform of a discharge pulses. The difference among them maybe useful to diagnose of insulation condition.
Data provided are for informational purposes only. Although carefully collected, accuracy cannot be guaranteed. The impact factor represents a rough estimation of the journal's impact factor and does not reflect the actual current impact factor. Publisher conditions are provided by RoMEO. Differing provisions from the publisher's actual policy or licence agreement may be applicable.