Partial Discharge Measurement and Cable Length: Meaning and Limits
Dept. of Electr. Eng., Univ. Bologna, BolognaDOI: 10.1109/ELINSL.2008.4570407 Conference: Electrical Insulation, 2008. ISEI 2008. Conference Record of the 2008 IEEE International Symposium on
Source: IEEE Xplore
Optimum detector bandwidth selection for partial discharge testing of high voltage power cables is discussed in this paper. The analysis is based on analytical models already described in literature, whose parameters have been validated by lab tests. The results indicate that when testing cables system on an accessory-per-accessory basis a detection bandwidth of few tens of MHz ensures: (a) large sensitivity to PD that could originate in the accessories as well as in the cable, (b) the capability of separating pulses coming from different parts of the power system and, thus, providing an approximate location of PD sources.
Conference Paper: On Line Partial Discharge Diagnosis of Power Cables[Show abstract] [Hide abstract]
ABSTRACT: This paper has the purpose to address in a practical way the topic of PD testing HV cables, with emphasis on on-line measurements and diagnostic interpretations. For this purpose, FAQ are discussed and examples reported of advantages and limitations of on-line PD testing.Electrical Insulation Conference, 2009. EIC 2009. IEEE; 07/2009
Data provided are for informational purposes only. Although carefully collected, accuracy cannot be guaranteed. The impact factor represents a rough estimation of the journal's impact factor and does not reflect the actual current impact factor. Publisher conditions are provided by RoMEO. Differing provisions from the publisher's actual policy or licence agreement may be applicable.